Payment & Shipping Terms:
20kVA Electronic Frequency Divider,
Electronic Multiple Frequency Divider,
Multiple Electronic Frequency Divider
The induction voltage test of the transformer and inductor is an important test to ensure the quality of the product. The test of voltage resistance between turns, interlayers, intersections, and phases of transformer windings is important in the transformer insulation test. The test of longitudinal insulation needs to press test voltage to the frequency doubling power, then be carried out. the results.
The ZXBP series of electronic multiple frequency deviser is designed to satisfy the above requirements. And it was confirmed by the vast number of users .
1. Small size, light weight, easy to carry and convenient for high power
2.not only produce third harmonic, but also produces test voltage output of 1, 2, 3, 4 frequency doubling.
3.Easy to operate and wiring,and reduce.the capacity demand of the field test.
2. Input voltage: AC:380V±10%,Three-phase,
(Note: the single-phase 220V can also be connected to the A and C ends of the power input, but the capacity at this time is almost halved)
3. Power frequency:50Hz.
4. Output voltage:0～400V (When the Step-up transformer is added, the voltage is rises, it needs to select a different configuration.)
5. Output frequency:50Hz,100Hz,150Hz,200Hz(alternative)
6. Harmonic distortion rate:<3%
Contact Person: Nie Qi