Payment & Shipping Terms:
|Fiber-optic Ethemet Interface:||3 Pairs*100/1000Mbits||Fiber-optic Serial Interface:||1 Pair*(2-10Mbits/s)|
|Synchronization Interface:||1 Pair*IRIG-B/PPS Fiber-optic Port||Eletrical Ethemet Port:||1pcs,RJ-45,100Mbits/s|
|Small Signal Output:||Can Be Customized||Binary Input:||Can Be Customized|
Intelligent Digital Relay Messages Analyzer,
Multifunctional Digital Relay Messages Analyzer,
Substation Handheld Relay Protection Tester
Relay Protection Tester
For Substation Handheld Intelligent Digital Relay Messages Analyzer
This device can be used for fast test of protection devices, intelligent terminals, merging units and transducers.
It is multi-functional with high precision and is essential equipment for installation, debugging, and maintenance of intelligent substation.
1. Capacitive mul-touch panel (5.7”), built in 11000mAh rechargeable li-battery, the continuous voyage ability over 6 hours
2. With 3 pairs optical Ethernet interface, 1 pair optical serial interface, 1 IRIG-B/PPS synchronous interface, support single-mode fiber connection
3. G-net interface for optical Ethernet interface, 100/1000Mbits/s self-adaptive
4. 2 channel hard switching input contact and 4 channel hard switching output contact, for intelligent terminal response testing
5. Support connection with USB storage device, for data import/export
6. Support IEC61850-9-1/2/LE,Goose,IEC60044-7/8 FT3,MMS,STNP,GRMP,IEEE-1588,IRIG-B,PPS,SCL standards.
7. Multi-functional, can test bay level, process level protection device, merging unit, intelligent terminal, mutual inducors.
8. Graph demonstration of various electrical parameters, direct result reading
9. A9+FPGA dual-core IPC performance, fast operation speed, message sending dispersion <0.1us, receiving time error <25ns
10. Small and portable, simple to use
Contact Person: Linda